Structural Integrity (SI) personnel visited a power plant construction site to examine four Grade 91 elbows (ASTM A234-WP91 20-inch OD Sch. 60) that were found to contain axially oriented surface indications. The elbows had not yet been installed. The indications were initially noticed during magnetic particle testing (MT) after one end of an elbow was field welded to a straight section and post weld heat treated (PWHT). Subsequently, three additional similarly welded elbows were inspected and indications were found at both the welded (inlet) and open (outlet) ends of three elbows. The elbow with the most significant indications was selected for SI’s on-site examinations. Figure 1 shows the inlet and outlet ends of the selected elbow.
Want to Read More? Complete the Form Below.