By: Wendy Weiss
Structural Integrity (SI) was recently asked to examine a fractured thermowell and determine the damage mechanism. The thermowell had been removed from bypass line piping in a heat-recovery steam generator (HRSG) that ran from the High Pressure (HP) bypass valve to the cold reheat section, and sent to the SI Materials Science Center. As reported by plant personnel, the fracture was located within the pipe wall. The pipe material was specified as ASME SA-335, Grade P22, and the thermowell was specified to be ASME SA-182, Grade F22.
Examination Procedure and Results
The fractured thermowell sections were visually examined and photographed in the as-received condition, as shown in Figure 1. The thermowell was comprised of two pieces: the thermowell housing itself which protruded into the steam stream, and a fitting connection to the pipe into which the thermowell housing was inserted.